After I presented details for selected days, I am going to review overall performance in the first year. From June 2015 to May 2016 ... … we needed 6.600 kWh of electrical energy in total. The heat pump consumed about 3.600 kWh of that ... … in order to 'pump it up to' 16.800 kWh … Continue reading First Year of Rooftop Solar Power and Heat Pump: Re-Visiting Economics
Our PV generator and new metering setup is now operational for half a year; this is my next wall of figures. For the first time I am combining data from all our loggers (PV inverter, smart meter for consumption, and heat pump system's monitoring), and I give a summary on our scrutinizing the building's electrical … Continue reading Half a Year of Solar Power and Smart Metering
In the previous post I gave an overview of our recently compiled data for the heat pump system. The figure below, showing the seasonal performance factor and daily energy balances, gave rise to an interesting question: In February the solar collector was off for research purposes, and the performance factor was just a bit lower … Continue reading Economics of the Solar Air Collector
We have updated the documentation of monthly and seasonal measurement data - now including also the full season September 2014 to August 2015. The overall Seasonal Performance Factor was 4,4 - despite the slightly lower numbers in February and March, when was the solar collector was off during the Ice Storage Challenge. Edit: I have … Continue reading Heat Pump System Data: Three Seasons 2012 – 2015
July 2015 was the hottest July ever since meteorological data had been recorded in Austria (since 248 years). We had more than 38°C ambient air temperature at some days; so finally a chance to stress-test our heat pump system's cooling option. Heating versus cooling mode In space heating 'winter' mode, the heat pump extracts heat … Continue reading Having Survived the Hottest July Ever (Thanks, Natural Cooling!)
No, my next project is not building a Perpetuum Mobile. Sometimes I mull upon definitions of performance indicators. It seems straight-forward that the efficiency of a wood log or oil burner is smaller than 1 - if combustion is not perfect you will never be able to turn the caloric value into heat, due to … Continue reading An Efficiency Greater Than 1?
The straight-forward way is to read off two energy values at the end of a period - day, month, or season: The electrical energy used by the heat pump and the heating energy delivered. The Seasonal Performance Factor (SPF) is the ratio of these - the factor the input electrical energy is 'multiplied with' to … Continue reading How to Evaluate a Heat Pump’s Performance?
Released from ice are brook and river By the quickening glance of the gracious Spring; The colors of hope to the valley cling, And weak old Winter himself must shiver, Withdrawn to the mountains, a crownless king. These are the first lines of the English version of a famous German poem on spring, from the … Continue reading Ice Storage Challenge: High Score!
We had considered it already a few years ago - when we decided to live and work in the middle of a dusty and noisy construction site for a few months: The upper part of the roof is inclined by 30° - which is the optimum angle for photovoltaic panels - whereas the windows in … Continue reading We Have Come a Long Way: Rooftop Solar Power Now!
I have received several questions related to my article on data logging on this blog, or to my postings on monitoring and control on our German blog. Thus I have decided to write the article I would have wanted to read when I once made myself familiar with this. The target audience for this article are … Continue reading Data Logging with UVR1611 – FAQ