Physicist, engineer, geek, dilettante science blogger, IT security consultant, search term poet, Subversive El(k)ement.

# Earth, Air, Water, and Ice.

In my attempts at Ice Storage Heat Source popularization I have been facing one big challenge: How can you – succinctly, using pictures – answer questions like:

How much energy does the collector harvest?

or

What’s the contribution of ground?

or

Why do you need a collector if the monthly performance factor just drops a bit when you turned it off during the Ice Storage Challenge?

The short answer is that the collector (if properly sized in relation to tank and heat pump) provides for about 75% of the ambient energy needed by the heat pump in an average year. Before the ‘Challenge’ in 2015 performance did not drop because the energy in the tank had been filled up to the brim by the collector before. So the collector is not a nice add-on but an essential part of the heat source. The tank is needed to buffer energy for colder periods; otherwise the system would operate like an air heat pump without any storage.

I am calling Data Kraken for help to give me more diagrams.

There are two kinds of energy balances:

1) From the volume of ice and tank temperature the energy still stored in the tank can be calculated. Our tank ‘contains’ about 2.300 kWh of energy when ‘full’. Stored energy changes …

• … because energy is extracted from the tank or released to it via the heat exchanger pipes traversing it.
• … and because heat is exchanged with the surrounding ground through the walls and the floor of the tank.

Thus the contribution of ground can be determined by:

Change of stored energy(Ice, Water) =
Energy over ribbed pipe heat exchanger + Energy exchanged with ground

2) On the other hand, three heat exchangers are serially connected in the brine circuit: The heat pump’s evaporator, the solar air collector, and the heat exchanger in the tank. .

Both of these energy balances are shown in this diagram (The direction of arrows indicates energy > 0):

The heat pump is using a combined heat source, made up of tank and collector, so …

Ambient Energy for Heat Pump = -(Collector Energy) + Tank Energy

The following diagrams show data for the season containing the Ice Storage Challenge:

From September to January more and more ambient energy is needed – but also the contribution of the collector increases! The longer the collector is on in parallel with the heat pump, the more energy can be harvested from air (as the temperature difference between air and brine is increased).

As long as there is no ice the temperature of the tank and the brine inlet temperature follow air temperature approximately. But if air temperature drops quickly (e.g. at the end of November 2014), the tank is still rather warm in relation to air and the collector cannot harvest much. Then the energy stored in the tank drops and energy starts to flow from ground to the tank.

On Jan 10 an anomalous peak in collector energy is visible: Warm winter storm Felix gave us a record harvest exceeding the energy needed by the heat pump! In addition to high ambient temperatures and convection (wind) the tank temperature remained low while energy was used for melting ice.

On February 1, we turned off the collector – and now the stored energy started to decline. Since the collector energy in February is zero, the energy transferred via the heat exchanger is equal to the ambient energy used by the heat pump. Ground provided for about 1/3 of the ambient energy. Near the end of the Ice Storage Challenge (mid of March) the contribution of ground was increasing while the contribution of latent energy became smaller and smaller: Ice hardly grew anymore, allegedly after the ice cube has ‘touched ground’.

Mid of March the collector was turned on again: Again (as during the Felix episode) harvest is high because the tank remains at 0°C. The energy stored in the tank is replenished quickly. Heat transfer with ground is rather small, and thus the heat exchanger energy is about equal to the change in energy stored.

At the beginning of May, we switched to summer mode: The collector is turned off (by the control system) to keep tank temperature at 8°C as long as possible. This temperature is a trade-off between optimizing heat pump performance and keeping some energy for passive cooling. The energy available for cooling is reduced by the slow flow of heat from ground to the tank.

# Frozen Herbs and Latent Energy Storage

… having studied one subject, we immediately have a great deal of direct and precise knowledge … of another.

Feynman referred to different phenomena that can be described by equations of the same appearance: Learning how to calculate the distribution of electrical charges gives you the skills to simulate also the flow of heat.

But I extend this to even more down-to-earth analogies – such as the design of a carton of frozen herbs resembling our water-tight underground tank.

No, just being a container for frozen stuff is too obvious a connection!

Maybe it is the reclosable lid covering part of the top surface?

No, too obvious again!

Or it is the intriguing ice structures that grow on the surface: in opened frozen herb boxes long forgotten in the refrigerator – or on a gigantic ice cube in your tank:

The box of herbs only reveals its secret when dismantled carefully. The Chief Engineer minimizes its volume as a dedicated waste separating citizen:

… not just tramping it down (… although that sometimes helps if some sensors do not co-operate).

He removes the flaps glued to the corners:

And there is was, plain plane and simple:

The Chief Engineer had used exactly this folding technique to cover the walls and floor of the former root cellar with a single piece of pond liner – avoiding to cut and glue the plastic sheet.

# On Photovoltaic Generators and Scattering Cross Sections

Subtitle: Dimensional Analysis again.

Our photovoltaic generator has about 5 kW rated ‘peak’ power – 18 panels with 265W each.

South-east oriented part of our generator – 10 panels. The remaining 8 are oriented south-west.

Peak output power is obtained under so-called standard testing condition – 1 kWp (kilo Watt peak) is equivalent to:

• a panel temperature of 25°C (as efficiency depends on temperature)
• an incident angle of sunlight relative to zenith of about 48°C – equivalent to an air mass of 1,5. This determines the spectrum of the electromagnetic radiation.
• an irradiance of solar energy of 1kW per square meter.

Simulated spectra for different air masses (Wikimedia, User Solar Gate). For AM 1 the path of sunlight is shortest and thus absorption is lowest.

The last condition can be rephrased as: We get 1 kW output per kW/minput. 1 kWp is thus defined as:

1 kWp = 1 kW / (1 kW/m2)

Canceling kW, you end up with 1 kWp being equivalent to an area of 1 m2.

Why is this a useful unit?

Solar radiation generates electron-hole pairs in solar cells, operated as photodiodes in reverse bias. Only if the incoming photon has exactly the right energy, solar energy is used efficiently. If the photon is not energetic enough – too ‘red’ – it is lost and converted to heat. If the photon is too blue  – too ‘ultraviolet’ – it generates electrical charges, but the greater part of its energy is wasted as the probability of two photons hitting at the same time is rare. Thus commercial solar panels have an efficiency of less than 20% today. (This does not yet say anything about economics as the total incoming energy is ‘free’.)

The less efficient solar panels are, the more of them you need to obtain a certain target output power. A perfect generator would deliver 1 kW output with a size of 1 m2 at standard test conditions. The kWp rating is equivalent to the area of an ideal generator that would generate the same output power, and it helps with evaluating if your rooftop area is large enough.

Our 4,77 kW generator uses 18 panels, about 1,61 m2 each – so 29 m2 in total. Panels’ efficiency  is then about 4,77 / 29 = 16,4% – a number you can also find in the datasheet.

There is no rated power comparable to that for solar thermal collectors, so I wonder why the unit has been defined in this way. Speculating wildly: Physicists working on solar cells usually have a background in solid state physics, and the design of the kWp rating is equivalent to a familiar concept: Scattering cross section.

An atom can be modeled as a little oscillator, driven by the incident electromagnetic energy. It re-radiates absorbed energy in all directions. Although this can be fully understood only in quantum mechanical terms, simple classical models are successful in explaining some macroscopic parameters, like the index of refraction. The scattering strength of an atom is expressed as:

[ Power scattered ] / [ Incident power of the beam / m2 ]

… the same sort of ratio as discussed above! Power cancels out and the result is an area, imagined as a ‘cross-section’. The atom acts as if it were an opaque disk of a certain area that ‘cuts out’ a respective part of the incident beam and re-radiates it.

The same concept is used for describing interactions between all kinds of particles (not only photons) – the scattering cross section determines the probability that an interaction will occur:

Particles’ scattering strengths are represented by red disks (area = cross section). The probability of a scattering event going to happen is equal to the ratio of the sum of all red disk areas and the total (blue+red) area. (Wikimedia, User FerdiBf)

# My Data Kraken – a Shapeshifter

I wonder if Data Kraken is only used by German speakers who translate our hackneyed Datenkrake – is it a word like eigenvector?

Anyway, I need this animal metaphor, despite this post is not about facebook or Google. It’s about my personal Data Kraken – which is a true shapeshifter like all octopuses are:

(… because they are spineless, but I don’t want to over-interpret the metaphor…)

Data Kraken’s shapeability is a blessing, given ongoing challenges:

When the Chief Engineer is fighting with other intimidating life-forms in our habitat, he focuses on survival first and foremost … and sometimes he forgets to inform the Chief Science Officer about fundamental changes to our landscape of sensors. Then Data Kraken has to be trained again to learn how to detect if the heat pump is on or off in a specific timeslot. Use the signal sent from control to the heat pump? Or to the brine pump? Or better use brine flow and temperature difference?

It might seem like a dull and tedious exercise to calculate ‘averages’ and other performance indicators that require only very simple arithmetics. But with the exception of room or ambient temperature most of the ‘averages’ just make sense if some condition is met, like: The heating water inlet temperature should only be calculated when the heating circuit pump is on. But the temperature of the cold water, when the same floor loops are used for cooling in summer, should not be included in this average of ‘heating water temperature’. Above all, false sensor readings, like 0, NULL or any value (like 999) a vendor chooses to indicate as an error, have to be excluded. And sometimes I rediscover eternal truths like the ratio of averages not being equal to the average of ratios.

The Chief Engineer is tinkering with new sensors all the time: In parallel to using the old & robust analog sensor for measuring the water level in the tank…

… a multitude of level sensors was evaluated …

… until finally Mr. Bubble won the casting …

… and the surface level is now measured via the pressure increasing linearly with depth. For the Big Data Department this means to add some new fields to the Kraken database, calculate new averages … and to smoothly transition from the volume of ice calculated from ruler readings to the new values.

Change is the only constant in the universe, paraphrasing Heraclitus [*]. Sensors morph in purpose: The heating circuit, formerly known (to the control unit) as the radiator circuit became a new wall heating circuit, and the radiator circuit was virtually reborn as a new circuit.

I am also guilty of adding new tentacles all the time, too, herding a zoo of meters added in 2015, each of them adding a new log file, containing data taken at different points of time in different intervals. This year I let Kraken put tentacles into the heat pump:

But the most challenging data source to integrate is the most unassuming source of logging data: The small list of the data that The Chief Engineer had recorded manually until recently (until the advent of Miss Pi CAN Sniffer and Mr Bubble). Reason: He had refused to take data at exactly 00:00:00 every single day, so learned things I never wanted to know about SQL programming languages to deal with the odd time intervals.

To be fair, the Chief Engineer has been dedicated at data recording! He never shunned true challenges, like a legendary white-out in our garden, at the time when measuring ground temperatures was not automated yet:

Long-term readers of this blog know that ‘elkement’ stands for a combination of nerd and luddite, so I try to merge a dinosaur scripting approach with real-world global AI Data Krakens’ wildest dream: I wrote scripts that create scripts that create scripts [[[…]]] that were based on a small proto-Kraken – a nice-to-use documentation database containing the history of sensors and calculations.

The mutated Kraken is able to eat all kinds of log files, including clients’ ones, and above all, it can be cloned easily.

I’ve added all the images and anecdotes to justify why an unpretentious user interface like the following is my true Christmas present to myself – ‘easily clickable’ calculated performance data for days, months, years, and heating seasons.

… and diagrams that can be changed automatically, by selecting interesting parameters and time frames:

The major overhaul of Data Kraken turned out to be prescient as a seemingly innocuous firmware upgrade just changed not only log file naming conventions and publication scheduled but also shuffled all the fields in log files. My Data Kraken has to be capable to rebuild the SQL database from scratch, based on a documentation of those ever changing fields and the raw log files.

_________________________________

[*] It was hard to find the true original quote for that, as the internet is cluttered with change management coaches using that quote, and Heraclitus speaks to us only through secondary sources. But anyway, what this philosophy website says about Heraclitus applies very well to my Data Kraken:

The exact interpretation of these doctrines is controversial, as is the inference often drawn from this theory that in the world as Heraclitus conceives it contradictory propositions must be true.

In my world, I also need to deal with intriguing ambiguity!

# Learning General Relativity

Math blogger Joseph Nebus does another A – Z series of posts, explaining technical terms in mathematics. He asked readers for their favorite pick of things to be covered in this series, and I came up with General Covariance. Which he laid out in this post – in his signature style, using neither equations nor pop-science images like deformed rubber mattresses – but ‘just words’. As so often, he manages to explain things really well!

Actually, I asked for that term as I am in the middle of yet another physics (re-)learning project – in the spirit of my ventures into QFT a while back.

Since a while I have now tried (on this blog) to cover only the physics related to something I have both education in and hands-on experience with. Re General Relativity I have neither: My PhD was in applied condensed-matter physics – lasers, superconductors, optics – and this article by physicist Chad Orzel about What Math Do You Need For Physics? covers well what sort of math you need in that case. Quote:

I moved into the lab, and was concerned more with technical details of vacuum pumps and lasers and electronic circuits and computer data acquisition and analysis.

So I cannot find the remotest way to justify why I would need General Relativity on a daily basis – insider jokes about very peculiarly torus-shaped underground water/ice tanks for heat pumps aside.

My motivation is what I described in this post of mine: Math-heavy physics is – for me, that means a statistical sample of 1 – the best way of brazing myself for any type of tech / IT / engineering work. This positive effect is not even directly related to math/physics aspects of that work.

But I also noticed ‘on the internet’ that there is a community of science and math enthusiasts, who indulge in self-studying theoretical physics seriously as a hobby. Often these are physics majors who ended up in very different industry sectors or in management / ‘non-tech’ jobs and who want to reconnect with what they once learned.

For those fellow learners I’d like to publish links to my favorite learning resources.

There seem to be two ways to start a course or book on GR, and sometimes authors toggle between both modes. You can start from the ‘tangible’ physics of our flat space (spacetime) plus special relativity and then gradually ‘add a bit of curvature’ and related concepts. In this way the introduction sounds familiar, and less daunting. Or you could try to introduce the mathematical concepts at a most rigorous abstract level, and return to the actual physics of our 4D spacetime and matter as late as possible.

The latter makes a lot of sense as you better unlearn some things you took for granted about vector and tensor calculus in flat space. A vector must no longer be visualized as an arrow that can be moved around carelessly in space, and one must be very careful in visualizing what transforming coordinates really means.

For motivation or as an ‘upper level pop-sci intro’…

Richard Feynman’s lecture on curved space might be a very good primer. Feynman explains what curved space and curved spacetime actually mean. Yes, he is using that infamous beetle on a balloon, but he also gives some numbers obtained by back-of-the-envelope calculations that explain important concepts.

For learning about the mathematical foundations …

I cannot praise these Lectures given at the Heraeus International Winter School Gravity and Light 2015 enough. Award-winning lecturer Frederic P. Schuller goes to great lengths to introduce concepts carefully and precisely. His goal is to make all implicit assumptions explicit and avoid allusions to misguided ‘intuitions’ one might got have used to when working with vector analysis, tensors, gradients, derivatives etc. in our tangible 3D world – covered by what he calls ‘undergraduate analysis’. Only in lecture 9 the first connection is made back to Newtonian gravity. Then, back to math only for some more lectures, until finally our 4D spacetime is discussed in lecture 13.

Schuller mentions in passing that Einstein himself struggled with the advanced math of his own theory, e.g. in the sense of not yet distinguishing clearly between the mathematical structure that represents the real world (a topological manifold) and the multi-dimensional chart we project our world onto when using an atlas. It is interesting to pair these lectures with this paper on the history and philosophy of general relativity – a link Joseph Nebus has pointed to in his post on covariance.

Learning physics or math from videos you need to be much more disciplined than with plowing through textbooks – in the sense that you absolutely have to do every single step in a derivation on your own. It is easy to delude oneself that you understood something by following a derivation passively, without calculating anything yourself. So what makes these lectures so useful is that tutorial sessions have been recorded as well: Tutorial sheets and videos can be found here.
(Edit: The Youtube channel of the event has not all the recordings of the tutorial sessions, only this conference website has. It seems the former domain does not work any more, but the content is perserved at gravity-and-light.herokuapp.com)

You also find brief notes for these lectures here.

For a ‘physics-only’ introduction …

… I picked a classical, ‘legendary’ resource: Landau and Lifshitz give an introduction to General Relativity in the last third of the second volume in their Course of Theoretical Physics, The Classical Theory of Fields. Landau and Lifshitz’s text is terse, perhaps similar in style to Dirac’s classical introduction to quantum mechanics. No humor, but sublime and elegant.

Landau and Lifshitz don’t need manifolds nor tangent bundles, and they use the 3D curvature tensor of space a lot in addition to the metric tensor of 4D spacetime. They introduce concepts of differences in space and time right from the start, plus the notion of simultaneity. Mathematicians might be shocked by a somewhat handwaving, ‘typical physicist’s’ way to deal with differentials, the way vectors on different points in space are related, etc. – neglecting (at first sight, explore every footnote in detail!) the tower of mathematical structures you actually need to do this precisely.

But I would regard Lev Landau sort of a Richard Feynman of The East, so it takes his genius not make any silly mistakes by taking the seemingly intuitive notions too literally. And I recommend this book only when combined with a most rigorous introduction.

I recommend Sean Carroll’s  Lecture Notes on General Relativity from 1997 (precursor of his textbook), together with his short No-Nonsense Introduction to GR as a summary. Carroll switches between more intuitive physics and very formal math. He keeps his conversational tone – well known to readers of his popular physics books – which makes his lecture notes a pleasure to read.

__________________________________

So this was a long-winded way to present just a bunch of links. This post should also serve as sort of an excuse that I haven’t been really active on social media or followed up closely on other blogs recently. It seems in winter I am secluding myself from the world in order to catch up on theoretical physics.

# Give the ‘Thing’ a Subnet of Its Own!

To my surprise, the most clicked post ever on this blog is this:

Network Sniffing for Everyone:
Getting to Know Your Things (As in Internet of Things)

… a step-by-step guide to sniff the network traffic of your ‘things’ contacting their mothership, plus a brief introduction to networking. I wanted to show how you can trace your networked devices’ traffic without any specialized equipment but being creative with what many users might already have, by turning a Windows PC into a router with Internet Connection Sharing.

Recently, an army of captured things took down part of the internet, and this reminded me of this post. No, this is not one more gloomy article about the Internet of Things. I just needed to use this Internet Sharing feature for the very purpose it was actually invented.

The Chief Engineer had finally set up the perfect test lab for programming and testing freely programmable UVR16x2 control systems (successor of UVR1611). But this test lab was a spot not equipped with wired ethernet, and the control unit’s data logger and ethernet gateway, so-called CMI (Control and Monitoring Interface), only has a LAN interface and no WLAN.

So an ages-old test laptop was revived to serve as a router (improving its ecological footprint in passing): This notebook connects to the standard ‘office’ network via WLAN: This wireless connection is thus the internet connection that can be shared with a device connected to the notebook’s LAN interface, e.g. via a cross-over cable. As explained in detail in the older article the router-laptop then allows for sniffing the traffic, – but above all it allows the ‘thing’ to connect to the internet at all.

This is the setup:

The router laptop is automatically configured with IP address 192.168.137.1 and hands out addresses in the 192.168.137.x network as a DHCP server, while using an IP address provided by the internet router for its WLAN adapter (indicated here as commonly used 192.168.0.x addresses). If Windows 10 is used on the router-notebook, you might need to re-enable ICS after a reboot.

The control unit is connected to the CMI via CAN bus – so the combination of test laptop, CMI, and UVR16x2 control unit is similar to the setup used for investigating CAN monitoring recently.

The CMI ‘thing’ is tucked away in a private subnet dedicated to it, and it cannot be accessed directly from any ‘Office PC’ – except the router PC itself. A standard office PC (green) effectively has to access the CMI via the same ‘cloud’ route as an Internet User (red). This makes the setup a realistic test for future remote support – when the CMI plus control unit has been shipped to its proud owner and is configured on the final local network.

The private subnet setup is also a simple workaround in case several things can not get along well with each other: For example, an internet TV service flooded CMI’s predecessor BL-NET with packets that were hard to digest – so BL-NET refused to work without a further reboot. Putting the sensitive device in a private subnet – using a ‘spare part’ router, solved the problem.

# And Now for Something Completely Different: Rotation Heat Pump!

Heat pumps for space heating are all very similar: Refrigerant evaporates, pressure is increased by a scroll compressor, refrigerant condenses, pressure is reduced in an expansion value. *yawn*

The question is:

Can a compression heat pump be built in a completely different way?

Austrian start-up ECOP did it: They  invented the so-called Rotation Heat Pump.

It does not have a classical compressor, and the ‘refrigerant’ does not undergo a phase transition. A pressure gradient is created by centrifugal forces: The whole system rotates, including the high-pressure (heat sink) and low-pressure (source) heat exchanger. The low pressure part of the system is positioned closer to the center of the rotation axis, and heat sink and heat source are connected at the axis (using heating water). The system rotates at up to 1800 rounds per minute.

A mixture of noble gases is used in a Joule (Brayton) process, driven in a cycle by a ventilator. Gas is compressed and thus heated up; then it is cooled at constant pressure and energy is released to the heat sink. After expanding the gas, it is heated up again at low pressure by the heat source.

In the textbook Joule cycle, a turbine and a compressor share a common axis: The energy released by the turbine is used to drive the compressor. This is essential, as compression and expansion energies are of the same order of magnitude, and both are considerably larger than the net energy difference – the actual input energy.

In contrast to that, a classical compression heat pump uses a refrigerant that is condensed while releasing heat and then evaporated again at low pressure. There is no mini-turbine to reduce the pressure but only an expansion valve, as there is not much energy to gain.

This explains why the Rotation Heat Pumps absolutely have to have compression efficiencies of nearly 100%, compared to, say, 85% efficiency of a scroll compressor in heat pump used for space heating:

Some numbers for a Joule process (from this German ECOP paper): On expansion of the gas 1200kW are gained, but 1300kW are needed for compression – if there would be no losses at all. So the net input power is 100kW. But if the efficiency of the compression is reduced from 100% to 80% about 1600kW are needed and thus a net input power of 500kW – five times the power compared to the ideal compressor! The coefficient of performance would plummet from 10 to 2,3.

I believe these challenging requirements are why Rotation Heat Pumps are ‘large’ and built for industrial processes. In addition to the high COP, this heat pump is also very versatile: Since there are no phase transitions, you can pick your favorite corner of the thermodynamic state diagram at will: This heat pump works for very different combinations temperatures of the hot target and the cold source.