Over the holidays I stayed away from social media, read quantum physics textbooks instead, and The Chief Engineer and I mulled over the fundamental questions of life, the universe and everything. Such as: How to explain our heat pump system?
Many blog postings were actually answers to questions, and am consolidating all these answers to frequently asked questions again in a list of such answers. However, this list has grown quickly.
An astute reader suggested to create an ‘animation’ of the gradual evolution of the system’s state. As I learned from discussions, one major confusion was related to the role of the solar collector and the fact that you have to factor in the history of the heat source: This is true for every heat pump system that uses a heat source that can be ‘depleted’, in contrast to a flow of ground water at a constant temperature for example. With the latter, the ‘state’ of the system only depends on the current ambient temperature, and you can explain it in a way not too different from pontificating on a wood or gas boiler.
One thing you have to accept though is how a heat pump as such works: I have given up to go into thermodynamical details, and I also think that the refigerator analogy is not helpful. So for this pragmatic introduction a heat pump is just a device that generates heating energy as an output, the input energy being electrical energy and heat energy extracted from a rather cold heat source somewhere near the building. For 8kW heating power you need about 2kW electrical energy and 6kW ambient energy. The ratio of 8kW and 2kW is called the coefficient of performance.
What the typical intro to heat pumps in physics textbooks does not point out is that the ambient heat source actually has to be able to deliver that input energy – during a whole heating season. There is no such thing as the infinite reservoir of energy usually depicted as a large box. Actually, the worse the performance of a heat pump is – the ratio of output heat energy and input electrical energy, the smaller are the demands on the heat source. The Chief Engineer has coined the term The Heat Source Paradox for this!
The lower the temperature of the heat source, the smaller the coefficient of performance is: So if you run an air source heat pump in mid-winter (using a big ventilator) then less energy is extracted from that air source than a geothermal heat pump would extract from ground. But if you build a geothermal heat source that’s too small in relation to a building’s heating demands, you see the same effect: Ground freezes, source temperature decreases, performance decreases, and you need more electrical energy and less ambient energy.
I am harping on the role of the heat source as the whole point of our ‘innovation’ is our special heat source that has two components, both of them being essential: An unglazed solar collector and an underground water / ice tank plus the surrounding ground. The solar collector allows to replenish the energy stored in the tank quickly, even in winter, and the tank is a buffer: When no energy is harvested by the collector at ambient temperatures below 0°C water freezes and releases latent heat. So you can call that an air heat pump with a huge, silent and mainentance-free ‘absorber’ plus a buffer that provides energy for periods of frost and that allows for storing all the energy you don’t need immediately. Ground does provide some energy as well, and I am planning to post about my related simulations. It can be visulized as an extension of the ice / water energy storage into the surroundings. But the active volume or area of ground is smaller than for geothermal systems as most of the ambient energy actually comes from the solar collector: The critical months in our climate are Dec-Jan-Feb: Before and after, the solar collector would be sufficient as the only heat source. In the three ‘ice months’ water is typically frozen in the tank, but even then the solar collector provides for 75-80% of the ambient energy needed to drive the heat pump.
Components are off-the-shelf products, actually rather simple and cheap ones, such as the most stupid, non-smart brine-water heat pump. What is special is 1) the arrangement of the heat exchanger in the water tank and 2) the custom control logic, that is programming of the control unit.
So here is finally the series of images of the system’s state, shown in a gallery and with captions: You can scroll down to see the series embedded in the post, or click on the first image to see an enlarged view and then click through the slide-show.
Information for German readers: This post contains the German version of this slide-show.